Stainless steel centrifugal pump in the operation of the sudden leakage is mostly due to changes in operating conditions or operation, improper maintenance caused.
1) Take the time, cavitation or a long time to suppress pressure, leading to seal damage;
2) The actual output of the pump is too small, a large number of media pump cycle, the accumulation of heat caused by media gasification, resulting in sealing failure;
3) For a long time outage, restart the manual when there is no manual car, friction due to adhesion and tear off the sealing surface;
4) Medium corrosive, polymerizability, gelatinous material increased;
5) Sudden changes in ambient temperature.
So Nanjing lanshen Pump Corp.LTD., to remind you, pay attention to the daily protection of the pump, do not have to start a long time to do the appropriate treatment, pay attention to the pump operating conditions
Users’ water consumption is generally dynamic, so water shortage or excess water situation occurs. And the imbalance between water and water is reflected in the water supply pressure, that is, water and water supply less, the pressure is low; water and water supply more, the pressure is large. Maintain the constant water supply pressure, so that water and water can be maintained between the balance, that is, water supply for many times, less water when the water is less, thus improving the quality of water supply.
Constant pressure water supply system is very important for users. In the production of domestic water supply, if the water supply for some reason or lack of water, may affect the quality of life, serious will affect the safety of survival, such as the occurrence of fire, if the water supply is insufficient or water supply, can not fire, Causing significant economic losses and casualties. Therefore, the water area is used constant pressure water supply system, can produce greater economic and social benefits.
With the development of power technology, frequency control technology is improving, with frequency control as the core of the intelligent water supply control system to replace the previous high water tank and pressure tank and other water supply equipment, starting smooth, starting current can be limited to within the rated current, Thus avoiding the impact of the start of the power grid; the average speed of the centrifugal pump is reduced, which can extend the life of pumps and valves and other things; can eliminate the start and stop when the water hammer effect. Its stable and safe operation performance, simple and convenient mode of operation, and complete and thoughtful function, will make water supply to achieve water, energy saving, saving manpower, and ultimately achieve efficient operation purposes.
Some users may not know the working principle of sewage pump, in fact, it is just a pump and motor connected with the work of the equipment, when used in the same time can be submerged work, compared with the general pump, there will be Greater work performance, and the footprint is relatively small, very easy to use when the large, large sewage pump can be automatically installed, the operation method is very simple in the installation of sewage pump, it can play a greater work Characteristics, of course, the quality of self-test sewage pump is also very important factor, you must know how to do the detection work, for the sewage pump operation methods, selection problems and other aspects of a certain understanding, which will make you better use the sewage pump, but also to check the direction of movement of the rotor, from top to bottom to see if the clockwise direction to run, to meet the normal use of performance, in order to confirm the quality of the sewage pump, Phase operation, if the fuse is found to break the phenomenon, be sure to check the reasons, and then put into use, through this method, there will be a greater use of results.
The deep well infusion techniques of deep well submersible pumps are extremely harmful to human health and the environment, and may minimize the risk of harm, as compared with other disposal technologies such as surface landfill, storage tank or incineration. Because it has the following advantages: Perfusion liquid stored in the deep geological layer, to avoid pollutants into the biosphere circulatory system; can reduce the atmospheric, water and shallow stratospheric environmental pressure; can replace the surface environmental capacity; when the environmental capacity is highly scarce And high processing costs, can reduce the cost of pollutant treatment; expand the scope of pollutant control technology selection. In all cases envisioned by the risk analysis, the risk of deep well infiltration is between one and one millionth of a million, and the safety factor is much higher than other waste disposal techniques.
Drainage pumps used in buildings are submersible sewage pumps, liquid sewage pumps, vertical sewage pumps and horizontal sewage pumps.
As the general site of the building is small, the displacement is not large, the drainage pump can give priority to the use of submersible sewage pump and liquid sewage pump, which liquid sewage pump is generally used in important places; vertical sewage pump and horizontal sewage pump requirements set Earthquake foundation, self-irrigation, and occupy a certain site, so use less in the building.
1.Use low noise water pump.
2.The pump unit should be set vibration device, the base should be installed under the rubber vibration pad, rubber vibration isolator, rubber shock absorber, spring shock absorber and so on. Refer to “Waterproof and installation of water pump and its installation Atlas” SS657.3, in the pump suction pipe and outlet pipe, should be set up vibration devices, such as flexible rubber joints.
4.Pipe stents and pipes through the wall, wear floor, should take anti-solid sound measures, such as the pump room with flexible hanger, elastic bracket or in the wall through the pipe and hole between the glass fiber.
5.If necessary, can be taken on the building sound insulation and sound absorption measures, such as the pump room with double glass doors and windows, walls, ceiling installation of porous sound-absorbing panels.
6.The basis of vibration isolation, pipe vibration isolation and vibration isolation vibration isolation area of the number of layers, the number and number of flexible joints must be calculated.
7.Fire dedicated pump.
Frequent use of submersible pump users will have encountered more or less tripping, then you will get the relationship between electricity, this must be caused by a short circuit, this is also a reason. In addition to a lot The reasons for the impact of submersible pump trip, you are not stable current or submersible pump switch bad contact and so on. But sometimes we found that these reasons are not.
There is also a problem with the cable of the submersible pump. Current transformer polarity is connected correctly. After troubleshooting the cause of the equipment failure and wiring errors, the differential protection operates during motor start, indicating that the differential current in the differential circuit exceeds the differential relay setting during this process. Above can be regarded as often cause submersible pump failure reasons, we can follow a certain order, overall troubleshooting first, then troubleshooting partial.
The upper part of the submersible motor shaft is equipped with a labyrinth sand control and two return-mounted skeletal seals to prevent flow sand from entering the motor. The submarine motor adopts water lubricated bearing, the lower part is equipped with rubber regulating film, regulating spring, regulating the pressure chamber, adjusting the pressure change caused by the temperature; the motor winding adopts polyethylene insulation, the nylon sleeve sets of water resistant magnetic wire, Cable connector technology, the connector insulation off scraping paint layer, were connected, welding firmly, with raw rubber around a layer. And then wrapped with waterproof adhesive tape 2-3 layer, the outer layer of 2-3 layers of waterproof tape or glue adhesive layer of rubber (bike tire) to prevent water seepage.
After the hub of the pump assembly coupling is assembled on the shaft, the vertical and coaxial degrees of the hub and the shaft should be carefully checked. Usually in the hub of the end and the outer circle set up two dial indicator, turning the wheel when the rotation, observe the hub of the whole beating (including the end of beating and radial run) values, determine the vertical axis and the axis of the axis and coaxial The situation of the situation. Different speed coupling of the requirements of the whole beating different values, different types of coupling on the requirements of the whole beating are also different, but the wheel assembly on the axis after the hub must be the total beating deviation of the value of Design requirements within the tolerance range, which is one of the main quality requirements of the coupling assembly.
Pump assembly caused by the hub of the total beating value does not meet the requirements of many reasons, the first may occur in the manufacturing process due to the error caused by processing for the field assembly, mainly due to correct the wheel hole surface treatment is not correct, so that the hub and axis concentric The degree of deviation. Another reason is that there is a key coupling in the assembly, due to improper assembly of the key caused by the hub and the shaft different axis. The correct installation of the key should be the key side of the key and the keyway wall tightly fit, usually in the assembly with color inspection, with a bad time can be used to repair the file or blade to meet the requirements. Key upper part of the general gap, about 0.1-0.2mm or so. High-speed rotating machinery for the hub and the axis of the coaxial degree of high demand, with a single bond can not get a high degree of coaxial, with double bond or spline connection can make the coaxial degree of both improved.
The minimum submerged depth of the pump is a prerequisite for proper operation of the pump. The samples on the factory are marked with clear data. The Panda pump indicates that the data is calculated on the basis of:
1. According to the pump’s abundance allowance calculation, to ensure that the pump does not occur cavitation.
2. For submersible pumps in the upper part of the motor, if the motor cooling cycle is not installed, the entire motor is immersed in water to cool the motor stator.
3. The minimum submerged depth is to ensure that the pump running, the sink does not occur in the whirlpool, the air is not involved in the import of the pump, and to ensure that the liquid flow into the pump evenly distributed.
Moreover, Nanjing lanshen Pump Corp.LTD. found that some pumping stations due to the flow and inhalation pool conditions are limited, the pump running after the change in the water level is very large, inhalation tank water level, resulting in the actual submerged depth below the minimum submerged depth, resulting in the pump can not run properly, Cavitation. Such as a pumping station, suction pool minimum water level elevation of 1m, up to 4.5m, water depth difference of 3.5m. If the pump station is designed according to the 1m elevation, the whole pumping station is dug deep and the elevation design is raised. The submerged depth is less than the minimum submerged depth.