1.Use low noise water pump.
2.The pump unit should be set vibration device, the base should be installed under the rubber vibration pad, rubber vibration isolator, rubber shock absorber, spring shock absorber and so on. Refer to “Waterproof and installation of water pump and its installation Atlas” SS657.3, in the pump suction pipe and outlet pipe, should be set up vibration devices, such as flexible rubber joints.
4.Pipe stents and pipes through the wall, wear floor, should take anti-solid sound measures, such as the pump room with flexible hanger, elastic bracket or in the wall through the pipe and hole between the glass fiber.
5.If necessary, can be taken on the building sound insulation and sound absorption measures, such as the pump room with double glass doors and windows, walls, ceiling installation of porous sound-absorbing panels.
6.The basis of vibration isolation, pipe vibration isolation and vibration isolation vibration isolation area of the number of layers, the number and number of flexible joints must be calculated.
7.Fire dedicated pump.
Frequent use of submersible pump users will have encountered more or less tripping, then you will get the relationship between electricity, this must be caused by a short circuit, this is also a reason. In addition to a lot The reasons for the impact of submersible pump trip, you are not stable current or submersible pump switch bad contact and so on. But sometimes we found that these reasons are not.
There is also a problem with the cable of the submersible pump. Current transformer polarity is connected correctly. After troubleshooting the cause of the equipment failure and wiring errors, the differential protection operates during motor start, indicating that the differential current in the differential circuit exceeds the differential relay setting during this process. Above can be regarded as often cause submersible pump failure reasons, we can follow a certain order, overall troubleshooting first, then troubleshooting partial.
The upper part of the submersible motor shaft is equipped with a labyrinth sand control and two return-mounted skeletal seals to prevent flow sand from entering the motor. The submarine motor adopts water lubricated bearing, the lower part is equipped with rubber regulating film, regulating spring, regulating the pressure chamber, adjusting the pressure change caused by the temperature; the motor winding adopts polyethylene insulation, the nylon sleeve sets of water resistant magnetic wire, Cable connector technology, the connector insulation off scraping paint layer, were connected, welding firmly, with raw rubber around a layer. And then wrapped with waterproof adhesive tape 2-3 layer, the outer layer of 2-3 layers of waterproof tape or glue adhesive layer of rubber (bike tire) to prevent water seepage.
After the hub of the pump assembly coupling is assembled on the shaft, the vertical and coaxial degrees of the hub and the shaft should be carefully checked. Usually in the hub of the end and the outer circle set up two dial indicator, turning the wheel when the rotation, observe the hub of the whole beating (including the end of beating and radial run) values, determine the vertical axis and the axis of the axis and coaxial The situation of the situation. Different speed coupling of the requirements of the whole beating different values, different types of coupling on the requirements of the whole beating are also different, but the wheel assembly on the axis after the hub must be the total beating deviation of the value of Design requirements within the tolerance range, which is one of the main quality requirements of the coupling assembly.
Pump assembly caused by the hub of the total beating value does not meet the requirements of many reasons, the first may occur in the manufacturing process due to the error caused by processing for the field assembly, mainly due to correct the wheel hole surface treatment is not correct, so that the hub and axis concentric The degree of deviation. Another reason is that there is a key coupling in the assembly, due to improper assembly of the key caused by the hub and the shaft different axis. The correct installation of the key should be the key side of the key and the keyway wall tightly fit, usually in the assembly with color inspection, with a bad time can be used to repair the file or blade to meet the requirements. Key upper part of the general gap, about 0.1-0.2mm or so. High-speed rotating machinery for the hub and the axis of the coaxial degree of high demand, with a single bond can not get a high degree of coaxial, with double bond or spline connection can make the coaxial degree of both improved.
Volume loss of centrifugal pump including seal ring leakage loss, balancing mechanism leakage loss and interstage leakage loss. This article describes the seal ring leakage loss.
In the entrance of the impeller is a seal ring, when the pump works, because the sealing ring on both sides with pressure difference between the side of the approximately impeller outlet pressure side of the impeller inlet pressure, so there will always be a part of the liquid from the impeller to the outlet impeller inlet leak. This part of the liquid in the impeller in obtaining energy, but the liquid did not sent, thus reducing the water supply pump. All the energy used to overcome the leakage of fluid resistance of the seal ring.
Obviously, if the sealing ring diameter larger ,pressure on both sides is more special, the greater the amount of leakage. For stereotypes pump, in order to improve feed efficiency of the pump leakage amount should be permitted in the case of the sealing ring gap is narrowing. Usually approximated total clearance seal ring diameter of 0.002, as Dw = 200 mm, the total clearance of 0.40 mm, when assembled, the sealing ring can not be eccentric too large, otherwise the amount of leakage also increases. The main measures In addition, the sealing ring can be used to increase the resistance method of reducing the amount of leakage, increase the resistance of the seal ring is made of a maze, zigzag, etc., which also increases the length of the sealing ring seal, increasing the resistance along the way.
Ring seal leakage, and in some cases cause disturbance of the impeller inlet, so will the rational design of the sealing ring form.
First, the submersible pump in the pump suction pipe set on the vacuum pump, pump start before the start of the vacuum pump, so that the first water pump filled with water to ensure that the pump automatically and quickly start. This type of water absorption requires a sound automatic control system to ensure proper operation.
Second, relative to the following are also relatively simple: no clogging submersible pump to reduce the water pipe corners, drop height and horizontal interval.
Third, this way need to set up a suction pipe in the pump, the pump in the first run before the tank should be filled with water, the first run after the end of the water tank due to the height of the water pipe height , Although the water level in the pool below the tank surface height, the tank of water will not turn back.
The last way to install the suction end valve at the end of the suction pipe of the submersible pump. The suction valve is actually a check valve, which ensures that the water can only enter the suction pipe from the pool and can not be reversed, so if the suction pipe is filled with water, although the pump axis elevation is higher than the working water level of the pool. The role of the end of the valve, the water pipe will not flow into the pool, the suction pipe has been filled with water, to ensure that the pump can automatically and quickly start.
The minimum submerged depth of the pump is a prerequisite for proper operation of the pump. The samples on the factory are marked with clear data. The Panda pump indicates that the data is calculated on the basis of:
1. According to the pump’s abundance allowance calculation, to ensure that the pump does not occur cavitation.
2. For submersible pumps in the upper part of the motor, if the motor cooling cycle is not installed, the entire motor is immersed in water to cool the motor stator.
3. The minimum submerged depth is to ensure that the pump running, the sink does not occur in the whirlpool, the air is not involved in the import of the pump, and to ensure that the liquid flow into the pump evenly distributed.
Moreover, Nanjing lanshen Pump Corp.LTD. found that some pumping stations due to the flow and inhalation pool conditions are limited, the pump running after the change in the water level is very large, inhalation tank water level, resulting in the actual submerged depth below the minimum submerged depth, resulting in the pump can not run properly, Cavitation. Such as a pumping station, suction pool minimum water level elevation of 1m, up to 4.5m, water depth difference of 3.5m. If the pump station is designed according to the 1m elevation, the whole pumping station is dug deep and the elevation design is raised. The submerged depth is less than the minimum submerged depth.
The impeller is made of cast or stamping, with high precision, high thrust, beautiful appearance, compact structure and compact structure. It adopts the multi-pole motor hybrid series products, direct coupling structure, low energy consumption and high efficiency.
The motor’s submersible mixer stirrer windings are class F insulated with protection class IP68. The use of sewage treatment plant aeration system, greatly reducing the system’s energy consumption, so that the oxygen content was significantly improved, and can effectively prevent. According to process requirements, direct diving mixing can be equipped with baffles.
1.Check the submersible gear box.
Submersible gearbox has high precision and good heat treatment, but it also has the phenomenon of gear teeth and the gear shaft is not axial clearance. We carried out a thorough cleaning of the gearbox and carefully examined gears, gear shafts, bearings. There is no pitting in the inner and outer ring and the surface of the roller, and the whole quality is good. The gears are smooth, no pitting, overlapping, normal backlash, no obvious wear on tooth profile. The radial and axial clearance are normal. Axial clearance is reasonable, hand wheel output shaft free flow, no interference, no abnormal sound. Therefore, the failure of the gearbox is eliminated.
2.Submersible mixer mechanical seal inspection
Mechanical seals are the most prone to failure of submersible fittings, often due to wear and tear of the mechanical seal failure, seal the cavity water. We first disassemble the mechanical seal assembly, which consists of two sets of mechanical seals, the skeleton oil seal, the output shaft, the bearing, the outer cover and the end cap and so on part to carry on the cleaning and the inspection, and inspects the bearing seat and the output shaft size, has not found. The mechanical seal is in place to eliminate the possibility of failure.
Suitable for industrial and municipal sewage treatment plants aeration tanks and anaerobic tanks, pool water cycle and nitrification, nitrogen and phosphorus removal.
Many industries will use submersible pumps, agricultural irrigation will also use submersible pumps, but the use of agricultural irrigation submersible pumps and most industries, after all, will be different. Now used to irrigate the drains of the land has been rare, but rather the more common submersible pumps for land irrigation, we will look at the use of agricultural submersible pump requirements.
Suitable for agricultural irrigation submersible pumps when installed, the pump should be ramped to reduce the elbow, or install the volute turn, so that the outlet can be facing the pool. As far as possible to shorten the submersible pump pipeline, we remove one meter of steel pipe, ten hours of irrigation work we can save 0.21 kg of diesel, a long time the greater the amount of diesel fuel savings, try to expand the submersible pump outlet diameter , If we put a four-meter-long 10 cm water hose into a 15 cm pipe, we can save 0.5 kg of petrol per ten hours.
In the submersible pump water can be kept clean, we can remove the filter. In order to prevent the impeller ring and axial clearance is not appropriate, we are in use, should be based on the submersible pump pump factory instructions to adjust, for submersible pumps in the pipeline blockage, we have to promptly clear, so as not to affect the submersible pump Normal work to prevent the submersible pump into the gas pump, because the pump intake will reduce the pump water, in order to prevent this situation, we should be in the submersible pump to check the various parts of the maintenance.
In response to the customers’ requirements, today we will introduce what is included in the sewage pump measurement accuracy
1.Sewage pump start, diesel engine start, emergency stop, increase or decrease;
2.Electric valve control (control flow);
3.Sewage pump conditions to switch to the implementation of the test process control;
4.Automatic start-up control of the cooling device;
5.Diesel engine water temperature, oil temperature, oil pressure and gear box oil temperature automatic monitoring and alarm.